# Tabele Proiect CCM

• View
62

0

Embed Size (px)

Transcript

Localitate: CALARASI 0 tev = 37.5 C = 23 % Az = 7 Np = 1/6 m2 qsp = w/m2 70 m2 Ldesen L= H= 4 m2 ql 0.055 kW qom = = = 2.14023E-05 hv 2569.82 hv = cp * t + 2501 = 1.86 * 37 + 2501 = 2569.82 0 0 (t = 4 10) C ti = tev - t ti = 37.5 - 10 = 27.5 C ti = (23 26)0C G = Np * qom v = D= tc = (6 8) 0C Q [kW] G [Kg/s] Q [kW] tc [0C] se adopta 8 0C Kg/s = Q [kW] ti - tc [0C) Kg/s Se adopta ti = 26 0C

Kg/s

m/s

tc = ti - tc tc = ti - tc = 26 - 8 = 18 0C hc = 44 [KJ/Kg] ti = 26 0C hi = 53 [KJ/Kg] hi - hc = 9 [KJ/Kg]

Tab. 1.1. Calcul tabelar distributrie aer proaspat:Nr. Crt. 5.4 1 2 3 4 5 6 7 8 9 destinatia Birou 1 Birou 2 Birou contorizare Birou S5 Apa Birou Tehnic 1 Birou Tehnic 2 Birou Auto Oficiu Portar Birou CAB ti [0C] 26 26 26 26 26 26 26 26 26 L [m] 5.85 5.80 5.80 3.00 5.80 5.80 5.80 2.75 3.00 S [m2] 31.59 31.32 31.32 16.2 30.45 30.45 23.59 6.46 15.75 Np buc 5 5 5 3 5 5 4 1 3 Q [W] 2211.30 2192.40 2192.40 1134.00 2131.50 2131.50 1651.30 452.38 1102.50 G [Kg/s] 0.00010701 0.00010701 0.00010701 0.00006421 0.00010701 0.00010701 0.00008561 0.00002140 0.00006421 v [[KJ/Kg] 20664.2 20487.5 20487.5 17661.7 19918.4 19918.4 19288.8 21136.8 17171.1

Tab. 1.2. Dimensionare retea distributie aer:m /h 594 1188 1782 2632 3226 4075 4925 5774 66243

Nr. Tr. 1 2 3 4 5 6 7 8 9

Debit l/s 165.0 330.0 495.0 731.0 896.0 1132.0 1368.0 1604.0 1840.0 m/s 0.165 0.330 0.495 0.731 0.896 1.132 1.368 1.604 1.840

v (impusa) m/s 6.50 7.00 7.50 8.00 8.50 9.00 9.50 10.00 10.50

S (rezultata) m 0.025 0.047 0.066 0.091 0.105 0.126 0.144 0.160 0.175

[mm] axh 125 x 200 240 x 200 350 x 200 460 x 200 550 x 200 650 x 200 750 x 200 800 x 200 850 x 200

S (reala) m 0.025 0.048 0.070 0.092 0.110 0.130 0.150 0.160 0.170

v (reala) m/s 6.60 6.88 7.07 7.95 8.15 8.71 9.12 10.03 10.82

Tab. 1.3. Selectare unitati de climatizare tip ventilo-convectori:Nr. Tr. 1 2 3 4 5 6 7 8 9 destinatia Birou 1 Birou 2 Birou contorizare Birou S5 Apa Birou Tehnic 1 Birou Tehnic 2 Birou Auto Oficiu Portar Birou CAB Q [KW] 2.21 2.19 2.19 1.13 2.13 2.13 1.65 0.45 1.10 Qsens [KW] 2.81 2.17 2.17 1.61 2.17 2.17 1.61 1.61 1.61 Debit apa l/h m/h 666 0.666 524 0.524 524 0.524 373 0.373 524 0.524 524 0.524 373 0.373 373 0.373 373 0.373 Debit aer m/h 610 445 445 380 445 445 380 380 380 tip. aparat ELVIRA ECM 32 ECM 22 ECM 22 ECM 12 ECM 22 ECM 22 ECM 12 ECM 12 ECM 12

Au fost selectati ventilo-convectori Elvira, tip caseta de plafon, cu 2 tevi, la o temperatura a apei 7 - 12 0C

Tab. 1.4. Dimensionarea conductelor pe distributia de agent termic si pierderile de sarcina aferente :Debit Qsens Nr. l/h [l/s] [KW] Tr. A. Distributia agentului termic pe ramura principala 1 373 0.104 1.61 2 746 0.207 2.71 3 1119 0.311 4.32 4 1643 0.456 6.49 5 2016 0.560 8.10 6 2540 0.706 10.27 7 3064 0.851 12.44 8 3730 1.036 15.25 9 4254 1.182 17.42 10 8508 2.363 34.85 Nota. Au fost selectate conducte de distributie din cupru. [mm] 22 x 1,2 28 x 1.2 28 x 1.2 35 x 1.5 35 x 1.5 42 x 1.5 42 x 1.5 42 x 1.5 42 x 1.5 54 x 1,5 R v l Rl

12.8 12.5 25 17.5 26 16 22 31 33 15

0.40 0.48 0.72 0.70 0.86 0.76 0.75 1.11 1.20 0.90

4.2 5.9 1.2 1.2 5.0 0.4 5.6 0.4 3.2 10.5

53.76 73.75 30 21 130 6.4 123.2 12.4 105.6 157.5

CALCULUL PIERDERILOR DE SARCINA PE TRONSOANE Tronson 1Nr. crt. Denumire ventilo-convector Robinet cu ventil si scaun oblic Cot drept TOTAL buc. 1 2 2 2.5 3.5 0.7 2.5 7 1.4 10.9

1 2 3

Tronson 2Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 3Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 4Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 5Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 6Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 7Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 8Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare TOTAL buc. 1 1 0.3 0.6 0.3 0.6 0.9

Tronson 9Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare 3 robinet sferic TOTAL buc. 1 1 0.3 0.6 0.3 0.6 1 1.9

2

0.5

Tronson 10Nr. Denumire crt. 1 teu trecere la separare 2 teu trecere la impreunare 3 robinet sferic buc. 1 1 4 0.3 0.6 0.5 0.3 0.6 2

4 5 6

Cot drept filtru "y" schimbator de caldura in placi TOTAL

6 1 1

0.6 2.5 3.5

3.6 2.5 3.5 12.5

Stabilirea inaltimii de pompare HRR' HRR'nec

Hpompa

nec

= (Rl+Z)c.c.m.d.

nec

= 1,7 [mCA]nom

Determinarea pompei de circulatie - se face in functie de : ( Q

, HRR' )

nec

Determinarea s-a facut folosind programul de selectie Willo cunoscand urmatoarele date: - Debitul vehiculat: Q = 8,5 [m3/h] - Inaltimea de pompare: H = 1,7 [mCA] - Fluid de lucru: apa rece la temp. de 7 [0C]

In urma selectiei a rezultat o pompa marca Willo, Stratos-E 40/1-4 CAN, 230 [V], 50 [Hz], PN 10, cu turatie variabila, ava - Debitul vehiculat: Q = 8,5 [m3/h] - Inaltimea de pompare: H = 1,7 [mCA]

Dimensionarea hidraulica a circuitelor racordate in paralel cu circuitul cel mai defavorizat (c.c.m.d.)Nr. Tr. 2.1 3.1 4.1 Qsens [KW] 1.61 1.61 2.17 Debit l/h 373 373 524 [l/s] 0.104 0.104 0.146 [mm] 22 x 1.2 22 x 1.2 22 x 1.2 R [mmcA/m] 12.8 12.8 24 v [m/s] 0.4 0.4 0.58 l [m] 2.6 1.2 3.9 Rl [mmcA] 33.28 15.36 93.6

A. Dimensionare hidraulica pe tronsoanele legate in paralel cu c.c.m.d.

5.1 6.1 7.1 8.1 9.1

1.61 2.17 2.17 2.81 2.17

373 524 524 666 524

0.104 0.146 0.146 0.185 0.146

22 x 1.2 22 x 1.2 22 x 1.2 28 x 1.2 22 x 1.2

12.8 24 24 10 24

0.4 0.58 0.58 0.43 0.58

3.7 3.9 2.7 3.9 2.7

47.36 93.6 64.8 39 64.8

CALCULUL PIERDERILOR DE SARCINA PE TRONSOANENr. trons on Ventilo-convector buc 1 1 1 1 1 1 1 1 2.5 2.5 2.5 2.5 2.5 2.5 2.5 2.5 Robinet cu ventil buc 2 2 2 2 2 2 2 2 3.5 3.5 3.5 3.5 3.5 3.5 3.5 3.5 buc 2 2 2 2 2 2 2 2 Cot drept 0.7 0.7 0.7 0.7 0.7 0.7 0.7 0.7 10.9 10.9 10.9 10.9 10.9 10.9 10.9 10.9

2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1

Verificare conditie (Rl + Z)x = (Rl + Z)r si calcul HRech (Z*rob)Nr. tr. 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1(Rl +Z)x [Pa] (Rl +Z)r [Pa] Z* echilibrare [Pa]

1204.8 1025.6 2778.1 1345.6 2778.1 2490.1 1392.8 2490.1

1409.6 2250.6 2784.6 3215.1 4925.5 5250.5 6736.8 7411.6

204.8 1225.0 6.5 1869.5 2147.4 2760.4 5344.0 4921.5

Pentru a se realiza echilibrarea hidraulica a circuitelor legate in paralel se va impune o pierdere de sarcina locala egala cu deficitul inregistrat pe fiecare circuit in parte (Z*). Echilibrarea consta in manevrarea ventilului cu ventil si scaun oblic montat pe fiecare consumator.

D [m3/h] 737.1 730.8 730.8 378.0 710.5 710.5 550.4 150.8 367.5

D [l/s] 204.8 203.0 203.0 105.0 197.4 197.4 152.9 41.9 102.1

tip. aparat tip 606 606 606 505 606 606 505 505 505

debit aparat [m3/h] 849.6 849.6 849.6 594 849.6 849.6 594 594 594

debit aparat [l/s] 236 236 236 165 236 236 165 165 165

v (impus) =(G/2)/(3.14*D2/4) =

6.835

e: Z Rl+Z (Rl+Z) Z 80 115 260 245 456 290 282.5 612 750 405

10.9 0.9 0.9 0.9 0.9 0.9 0.9 0.9 1.9 12.5

872 103.5 234 220.5 410.4 261 254.25 550.8 1425 5062.5

1409.6 841 534 430.5 1710.4 325 1486.25 674.8 2481 6637.5

1409.6 2250.6 2784.6 3215.1 4925.5 5250.5 6736.75 7411.55 9892.55 16530.05

u turatie variabila, avand urmatoarele caracteristici:

Z [Pa] 872 872 1842.1

Rl+Z [Pa] 1204.8 1025.6 2778.1 Z 80 80 169

10.9 10.9 10.9

10.9 10.9 10.9 10.9 10.9

872 1842.1 1842.1 1002.8 1842.1

1345.6 2778.1 2490.1 1392.8 2490.1

80 169 169 92 169

Localitate: ALEXANDRIA 0 tev = C 38 = Az = Np = qsp = 25 7 %

m2 1/6 75 w/m2 Ldesen + 1 m2 L= H= 4 m2 ql 0.055 kW qom = = = 2.1402E-05 hv 2569.82 hv = cp * t + 2501 = 1.86 * 37 + 2501 = 2569.82 0 (t = 4 10) C ti = tev - t ti = 38 - 10 = 28 0C ti = (23 26) C G = Np * qom Q [kW] v= G [Kg/s] Q [kW] D= tc [0C]0

Kg/s

Se adopta ti = 26 C m3/h 850 1699 2293 34810

0

Kg/s =0

Q [kW] ti - tc [0C)

Kg/s

m/s

tc = (6 8) C0

0

se adopta 8 C

tc = ti - tc tc = ti - tc = 26 - 8 = 18 C hc = 32 [KJ/Kg] ti = 26 C hi = 39 [KJ/Kg] hi - hc = 7 [KJ/Kg]

4669 5857 7045 8233 9421

1 2 3 4 5 6 7 8 9

A. Dimensionar1 2 3 4 5 6 7 8 9 10

Nr. crt.

1 2 3

Nr. crt. 1 2

Nr. crt. 1 2

Nr. crt. 1 2

Nr. crt. 1 2

Nr. crt. 1 2

Nr. crt. 1 2

Nr. crt. 1 2

Nr. crt. 1 2

3

Nr. crt. 1 2 3 4 5

6

Stabilirea ina HRR' HRR'nec

Hp = 1,9

nec

Determinarea s

In urma selecti

Dimensionare

A. Dimensionar2.1 3.1 4.1 5.1

6.1 7.1 8.1 9.1

2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1

2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1

Tab. 1.1. Calcul tabelar distributrie aer proaspat:Nr. Crt. 1 2 3 4 5 6 7 8 9 destinatia Birou 1 Birou 2 Birou contorizare Birou S5 Apa Birou Tehnic 1 Birou Tehnic 2 Birou Auto Oficiu Portar Birou CAB ti [0C] 26 26 26 26 26 26 26 26 26 L [m] 6.85 6.80 6.80 4.00 6.80 6.80 6.80 2.75 4.00 S [m2] 36.99 36.72 36.72 21.6 35.7 35.7 28.84 6.46 21.00 Np buc 6 6 6 4 6 6 5 1 4 Q [W] 2774.25 2754.00 2754.00 1620.00 2677.50 2677.50 2163.00 484.69 1575.00 G [Kg/s] 0.00012841 0.00012841 0.00012841 0.00008561 0.0001